Comes in 10 or 25kg drum (Liquid chemical)
DECHLOR S14 can be used for the de-chlorination of waste waters with the removal of excess chlorine after chlorination of water systems and cooling towers.
Can be dosed directly into the water to be treated. Typically used in conjunction with our FEEDCHLOR chlorine based product.
For every m3 of water use 14ml of Dechlor per 1ppm of Chlorine.
How to use it
DECHLORINATION OF TANKS
Where it is necessary to remove the excess chlorine from a volume of water prior to discharge to sewer, this can be achieved using DECHLOR S14
The DECHLOR S14 should be added at the rate of 14ml per ppm of Chlorine per m3 of water.
Example To remove 30 ppm of free residual chlorine in a 60m3 tank requires:-
14(ml) x 30(ppm) x 60(m3)
= 25,200 ml or
= 25.2 litres of DECHLOR S14
N.B. It is important not to over dechlorinate since this will absorb any free chlorine residual in the incoming main.
Feedchlor – a stronger chlorine solution suitable for potable water and swimming pools.
RO-DECL– a dechlorination solution suitable for Reverse Osmosis systems (Dechlor is unsuitable)