Cooling Tower Cleaning & Disinfection
In order to minimise the risk of Legionnaires’ disease and comply with the requirements of ACoP L8 a cooling tower chemical treatment should be performed in order to clean and disinfect the system regularly to remove fouling that can provide a growth environment for Legionella bacteria. The normal process involves Cooling Tower Chlorination incorporating additional bio-dispersant, physical cleaning and then a further post chlorination before the system is returned safely to service. Where practical and within the agreed scope of works, the cooling tower packing may be removed for additional inspection and cleaning. Feedwater also has experience in cleaning Hyperbolic cooling towers, enquire to find out more.
Feedwater also offer a unique service, foam cleaning cooling towers, a highly effective disinfection method incorporating Activ-Ox®, our patented Chlorine Dioxide chemistry, which is ideal for in-situ disinfection and cleaning of cooling tower packing. A full report of all works is produced identifying areas requiring remedial action and, where required, a photographic report showing the cooling tower condition.
Download our Activ-Ox Foam Cleaning Leaflet here
Cooling Tower Maintenance Repair and Refurbishment
We provide a comprehensive inspection service and can carry out any necessary cooling tower repairs. Cooling tower refurbishment may include, as appropriate, the replacement of air inlet louvres, drift eliminators, cooling tower packing / fill, repairs to the distribution systems, replacement of spray nozzles, fan repairs and sump painting / coating. If you feel like doing it yourself we can provide a full range of cooling tower packing, drift eliminators and other components at competitive prices.